DRN 6KA 1P+N RCD
DRNL earth leakage circuit breaker elcb electric shock,overload,short circuit protection are mainly applied to the AC 50/60Hz circuit rated 240V and 32A or below. DRNL elcb electric shock,overload,short circuit protection have the electric leakAge(electric shock),overload,short circuit and so on protection functions. The over voltage protection functions.The over voltage protection function can also be provided upon requirements. DRNL earth leakage circuit breaker elcb electric shock,overload,short circuit protection are mainly used to protect the buiding illumination and power distrion system.
AS/NZS 61009 - 1
Magnetic tripping characteristics
Residual tripping characteristics
6 - 32
Rated residual current
10mA, 30 mA
Rated voltage 1P
Maximum service voltage
Line & Load
Residual making and breaking capacity
Short circuit capacity
Isolation application (IEC 60947-2)
Insulation resistance (Mohm)
Insulation voltage (V)
Dielectric rigidity (V)
Endurance (operations) electrical
Protection degree outside
Self extinguishing degree (UL 94)
Tropicalisation (IEC 60068-2)
Terminal capacity (top & bottom) min / max
Terminal torque (top / bottom)
Features & Advantages:
◇Top and bottom line and load compatible newest design for ease of installation.
◇ Two pole safety feature allows switching of both Active and Neutral contacts.
Active contacts always connect earlier and break later;
◇ Single module is ideal to save valuable switchboard space.
Normal Operation Conditions
Ambient Air temperature:Ambient air temperature range from -5℃ ~+40℃ ,not exceeding 35℃ averagely in 24 hours.
Location:installation location can not exceed 2000 meters above sea level.
Air conditons:Relative humidity in the installation palce can not exceed 50% when the air reaches the highest temperature +40℃ ,the average minimum temperature when it is the wettest can not exceed 25℃ Relative humidity not exceeding 90%.
Installation conditions:Magnetic field outsid the installation place can not exceed 5 times of the site of terrestrial magnetism in all directions.Normally speaking,RCBO should be mounted vertically .If the operation handle puts through power source upward,there should be no notable impact and vibration in the installation place.
LeakAge protection function of RCBO is tested and adjusted by the manufacture,users can not open the products at random during usage.
After using RCBO for a certain time(normally one month) , test button should be pressed noce in a state of making the circuit to check whether the function of RCBO is normal and reliable(press test button once, the RCBO can break off noce) . If abnormal, it should be unloaded and sent to the manufacturer to repair.
RCBO can not be wetted or soaked by rain,snow or water during the course or transportation storage and usage.
Electrical Diagram & Installation:
Overall & installation dimensions