HROB-5.3 Lightning rod
Lightning rod with ESE (Early Streamer Emission) system.
Active protection. HRESE lightning rods with ESE (Early Streamer Emission) technology are designed and
manufactured according to state-of-the art technology in AISI 316 stainless steel.
The impact of the lightning strike takes places at a point above the tip of the rod thanks to the ESE technology.
This means a larger radius of protection and it enhances the cost efficiency of the lightning protection system
(LPS) as compared to passive systems.
Instruction of Use
(A)The installation of lightning rod
Matters need attention during installation:
(1)The lightning rod and other metal part on the building should connected together
(2)No low voltage cable or communication cable installed on the rod
(B)Installation of earthing tape and earthing grid
1.Installation of exposed earthing tape (grid) :Installed at the ridge ,eave(abat-vent) or edge of roof
(2)Installation on the parapet wall or gutter bracket
Installed along parapet wall and fixed with bracket ,and the bracket should be installed earlier .
The working height of bracket should be less than 150mm . The bracket for direct line should be first and then for
the middle .The bracket should be 0.25-0.5m away to the turning point if turning needed .
The horizontal spacing of bracket is 1-1.5m ,and vertical interval is 1.5-2m and even distribution
(3)Installation at ridge,eave or edge of roof
Use concrete base or bracke
If make the base on site , please remove the corner of ridge tile first ,and make the bracket and ridge tile together
The bracket should be 0.25-0.5m away to the turning point if turning needed .
The horizontal spacing of bracket is 1-1.5m ,and vertical interval is 1.5-2m and even distribution.